TrolMaster Environmental Sensor Calibration -- CO2
To calibrate the CO2 sensors on the TrolMaster controllers, we recommend using the “outdoor ambient air” method. Outdoors the CO2 level around the world is approximately 410ppm in the year 2021. If the CO2 sensor is operated outdoors, it should always read about 390-430ppm. Follow the process below to first check, and then recalibrate the CO2...